Detuned Reactor are used, in supply networks having a high level of harmonic distortion, when the final objective is reactive power compensation at the fundamental frequency.
Detuned Reactor are used, in supply networks having a high level of harmonic distortion, when the final objective is reactive power compensation at the fundamental frequency. Their purpose is to avoid the harmonic currents overload to the capacitors by diverting them to the mains. Protection filters are made by connecting reactors in series with capacitors, in such a way that the tuning frequency of the whole unit is set at a value between the fundamental frequency and the frequency of the lowest present harmonics, which is usually the 5th order harmonic. In this the filter has a high inductive impedance for all the harmonic frequencies.
Detuned, Iron Core, Copper or Aluminum Wound
From 5 KVAR to 100 KVAR
Filter Factor 5.67 % , 7 % , 14 %
- Application:- Power Factor correction Panels (In series with Capacitors)
- Purpose:- To avoid resonance by connecting Capacitors
- Range : From 5 KVAR to 300 KVAR
- Percentage Impedance:- 5.67 % , 7 % , 14 %
- Standard:- IS 5553
- Linearity:- 140-210%
- Insulation Class:- F/H
- Voltage:- 110-690V
- Phase:- 1/3
- Conductor Material:- Al/Cu(Foil & Conductor)
- Lamination:- CRNO/CRGO